CJ1W-PRM21 Omron Automation and Safety Controllers CJ1 Profibus Master datasheet, inventory, & pricing. This article (NJ base) explains how to setup the configuration for the NJ with a CJ1W-PRM21 Profibus communication unit connecting. Buy Omron CJ1W Series PLC I/O Module, 31 x 90 x 68 mm CJ1W-PRM Browse our latest plc-i-o-modules offers. Free Next Day Delivery.
|Published (Last):||22 April 2015|
|PDF File Size:||15.62 Mb|
|ePub File Size:||20.98 Mb|
|Price:||Free* [*Free Regsitration Required]|
Hello Daniel, Thanks for your answer. I was sure that I’ve tried all but I didn’t. In the front of the module apeare that is the version 2. I also programed the functions send and recv acording with the master configuration. What about those errors? But it’s possible that the problem is the hardware config. Hello Ariel; In your diagnostic messages a few stand out, at first prj21 ArielP 10!!
Create an account or sign in to comment You need prrm21 be a member in order to leave a comment Create an account Sign up for a new account in our community. Share this post Link to post Share on other sites.
I have no idea. But still I can’t scan in order to find connected slaves.
Started by malyalewariat18 March. The GSD file you will find here: I don’t have this software installed on pc Sign in Already have an account? The number of bytes its going to recive and send. Sign up for a new account in our community. Started by malyalewariat18 March prm21 cj1w bus profibus. Seeing the scan returns error with DTM version 1. When I use “Test” option or just go online I get errors: I’ve set up correct connection parameters of cj1w-prm profibus master.
I can now use diagnostic option and I can see states of plc and module.
CX-Configurator CJ1W-PRM21 connection problems.
I’m almost sure that this bosch unit provides profibus connection. Hope this helps, Daniel Chartier. So many communication protocols to choose. If this is already done, it would be good to see how they have been configured.
I made a diagnostic to de cp and appear this error: Try to run the Cj1s so you’ll get a newer version if you have a registered copy. Register a new account. Site Explorer Site Explorer. Edited 21 March by malyalewariat.
The module was update to firmware V3, but I have only in step 7 the product versions 1 and 2. I configured in S7 project the slave parameters. I should do any thing else, Thaks. You need to be a member c1jw order to leave a comment. Following DTM reported the error: Follow us on Twitter Youtube. I’ve made mistake, because communication module is diffirent than I mentioned before. This contribution was helpful to 1 thankful Users dchartier.
Hello, the BF led blink in the omron master, the slave appear only with the led run. The master tell me that the slave have a invalid response. All about Decentral Peripherie.
It supposed to be toolbus usb in configuration tab, and now i can use test, and go online options without any errors. It is profibus slave. Posted 21 March edited. When i try to use scan option i get another error:. What I can do. Have a look at the following FAQ and attached links: Hello Ariel; You seem to have had difficulty in uploading your diagnostic information.
Product Support Services Forum mySupport. Sign In Sign Up. Am I missing CX-Server? I uploaded the file already.